STATE OF CALIFORNIA, PETE WILSON, Governor
June 29, 1998
RE: Variance Request #90 - Reduce the refueling distance requirements (0.25 miles) stipulated by Mitigation Measure B-AQ-1 at the Compton Creek bore, City of Los Angeles, Segment 4B.
Dear Mr. Shauers:
We have reviewed the above-referenced variance request, and approve your request based on the following factors:
In order to refuel equipment in accordance with Mitigation Measure B-AQ-1 (greater than 0.25 miles from streams/creeks) construction equipment required for the boring operation would need to be removed from the bore pits and returned along the right-of-way to a location that meets the refueling criteria. Such an operation could delay construction and increase associated construction impacts (air quality, traffic, noise, safety).
As proposed under Variance Request #90, refueling would occur along the project right-of-way at the Compton Creek bore near station number ES 99+41 using established refueling procedures approved for five directional drill locations (see Variance Requests #35 and 66) and at the Dominguez Channel bore (see Variance Request #56).
Compton Creek is concrete-lined at the proposed location; thereby, preventing the migration of any potential spills from the surrounding soils into the waterway. In addition, existing topography to the east of the proposed refueling site would prevent a spill from reaching the waterway via overland flow. Finally, if a spill were to occur within a bore pit, it would be contained.
The measures noted below shall be implemented:
- All applicable mitigation measures for the project shall be implemented at the subject location.
- The following fueling kit shall be installed around each piece of equipment fueled within the 0.25 mile zone. The kit shall consist of an 8 by 8-foot area of plastic sheeting placed underneath or adjacent to the vehicle and the refueling truck. A 3 by 3-foot by 6-inch deep pan shall be placed underneath the vehicle being refueled. Each refueling truck shall also be equipped with automatic shutoff nozzles to prevent spillage from overtopping. In addition, absorbent material shall be placed around the filler pipe and the fueler shall be present throughout the entire fueling operation.
- Each refueling truck shall contain a fully stocked spill containment kit which includes absorbent pads, shovels, and appropriate spill containers.
- This variance approval allows for refueling and routine maintenance only at the approved location and only if the stipulated measures are implemented. Storage of fuel or other hazard materials, or vehicle/equipment repair shall not be allowed under the provisions of this variance.
- All drips, leaks, and/or spills from vehicles and/or equipment shall be excavated immediately and disposed of in appropriate, labeled containers.
- Parking of refueling trucks at the subject site shall be prohibited.
- Implementation of this variance in accordance with the provisions noted above shall be verified on a random basis by a CPUC/ANF Environmental Monitor.
Back to Variances Pages
Back to MMCRP Home Page