General Order 95
Detailed Construction Requirements for Supply Lines
(Class H, L and T Circuits)
Where mechanical loads imposed on poles, towers, or structures
are greater than can be supported with safety factors as specified in
, additional strength shall be provided by the use of guys or other suitable
Where guys are used with poles or similar structures capable of considerable deflection before failure, the guys shall be able to support the entire load, the pole below the point of guy attachment acting merely as a strut.
Guys shall be attached to structures, as nearly as practicable, at the center of load. They shall be maintained taut and of such strength as to meet the safety factors of Rule 44 .