General Order 95
Detailed Construction Requirements for Supply Lines
(Class H, L and T Circuits)
56.9 Guy Marker (Guy Guard)
A substantial marker of suitable material, including but not
limited to metal or plastic, not less than 8 feet in length, shall be securely
attached to all anchor guys. Where more than one guy is attached to an anchor
rod, only the outermost guy is required to have a marker.
Note: Revised September 15, 1964 by Decision No. 67820, November 21, 1990 by Resolution SU–6 and October 9, 1996 by Resolution SU–40.