General Order 95
Detailed Construction Requirements for Supply Lines
(Class H, L and T Circuits)
Time Switches, Meters, Metal Boxes, Other Apparatus and Associated
A. Grounded (See
Time switches, meters, metal boxes, other apparatus and associated antennas are not allowed in the climbing space.
C. Within 8 Feet of the Ground
Boxes or enclosures containing switches, meters, or other apparatus having accessible live parts, which are located 8 feet or less above the ground shall be effectively locked or sealed.
Metal boxes which contain supply or control equipment or conductors and are located 8 feet or less above the ground shall be effectively grounded.
Note: Revised January 19, 1994 by Resolution SU–25.