General Order 95
Detailed Construction Requirements for Tower Lines
and Extra High Voltage Lines (Class E Circuits)
The basic minimum clearances of overhead guys above the ground and from other wires or cables are specified in Tables 1 and 2 . modifications of these basic clearances are specified in Rules 37 And 38 . The minimum clearance of 18 feet for overhead guys of high voltage supply lines shall not be decreased along public thoroughfares or railways.
For clearances of anchor guys from overhead guys, span wires and conductors supported on other poles or structures, see Rule 56.4 .